Double Block and Bleed Systems
The primary function of a double block and bleed system is for isolation and the secondary function is for intervention.
Under certain conditions double block and bleed systems are needed to prevent product contamination or where it is necessary to remove essential equipment from service for cleaning or repairs while the unit continues in operation.
Of course, such equipment must be provided with a spare or it must be possible to bypass it temporarily without shutting down the unit.
The nature of the fluid, its pressure and temperature, and many other factors must be considered when determining the need for double block and bleed systems.
Generally, block Valves should be considered for the onstream isolation of equipment if the fluid is flammable or otherwise hazardous, or if the fluid is in high-pressure or high-temperature service. Where double block Valves are used, a NPS 3/4 or larger bleed Valve should be installed between the block Valves.
The purpose of the bleed Valve is twofold. First, the bleed ensures that the upstream Valve is in fact tight before slipping in a blind off the downstream block Valve. The bleed connection also permits the safe withdrawal of moderate leakage from the upstream Valve to again assure the tight shutoff of the downstream Valve.
Depending on the service conditions, it may be possible to use a single block Valve with a body bleed to provide double block and bleed provisions for onstream isolation of equipment.
Gate Valves with flexible wedges and with body or Bonnet bleed Valve can serve this purpose if specifically tested in accordance with API-598 for double block and bleed quality Valves.
Some Ball Valves and nonlubricated Plug Valves, when equipped with a Valve body bleed between the seats, can also be satisfactory substitutes for double block Valves.
Testing for double block and bleed quality Valves requires the pressure-testing of each seat, with leakage measured through the Valve body bleed as a means of substantiating the independent leak tightness of both the upstream and downstream seats of the Valve.
Double Block and Bleed Valves
The Double Block and Bleed Valve or a DBBV can perform the tasks of 3 separate Valves (2 separate isolations and 1 drain Valve) which apart from being hugely space saving can also save on weight and time due to installation and maintenance practices requiring much less work and the operator being able to locate and operate all 3 Valves in one location.
Double block and bleed Valves operate on the principle that isolation can be achieved from both the upstream and downstream process flow / pressures.
This is achieved by two ball, gate, globe, needle, etc. Valves placed back to back, with a third "isolatable" Valve in the centre cavity.
Once isolation has been achieved in one or more of the main process isolation Valves, the cavity that is created between these isolations can be drained. This is useful for flow diverting, sampling or injection situations, and for maintenance and or integrity check situations where seat leakage can be monitored through the third "bleed" Valve.
The image on the left gives you a good impression, how a DBB Valve is constructed.
In this image example, three balls are mounted. 2 large balls that serve as a block (both are closed), and the small ball serve as the bleed (ball is in open position).
Image comes from www.habonim.com. It is a DBB Valve in the dual-Safe series. For more information about Habonim click the PDF icon below.
Double Block & Bleed Valves
Isolation (Stop) Valves in Pressure-Relief Piping
The article below (text) comes from the American Petroleum Institute (API)
Sizing, Selection, and Installation of Pressure-Relieving Devices in Refineries, Part II-Installation
API recommended practice 520 fifth edition
True meaning of Double Block and Bleed
Rudy Garza, Mechanical Lead-Static Equipment Engineering Group at ExxonMobil Development Company, gave a presentation at the VMA Technical Seminar in San Antonio entitled "Isolation Philosophies" in which he asserted that many people take the term "Double Block & Bleed" (DBB) to mean the same thing as Double Positive Isolation" (DPI).
It's time to do maintenance on a section of process. You don't want to shut down the entire facility, so you decide to block off and depressurize just the section you're working on. Just upstream is a double block and bleed Valve - a trunnion-mounted Ball Valve with self-relieving seals and a bleed Valve to vent the cavity. You close the Ball Valve and open the bleeder. Now you can de-pressurize the line downstream and open it up to work on it.
No so fast, says Rudy Garza. You may think that Valve gives you double isolation, but it doesn't and that could be dangerous....More on the next page